> To:  Paul Y'Barbo
> 
> From: Chuck Thompson	
> 
> Subject: Rio Puerco Operating Issues
> 
> 
> Here's the "quick and dirty" on the strategies discussed on Monday....
> 
> *	Look at the TW 10" as the primary run..... investigate the
> possibility of installing 1/4" (thickness) orifice plates in both TW
> runs....If 1/4" plates are not possible, investigate meter run
> change-outs....TW to speed up the pid response on the "mushroom"
> regulators....
> *	Take the TW "mushrooms" out of service and PNM to provide
> flow-control.... take the TW positive shut-in valve out of service.... PNM
> to provide shut in sequence with minimum flow parameters to be set at
> approx 12,000 - 15,000 mcfd rate....
> *	Investigate joint venture ultrasonic installation.
> 
> Sorry for the delay in getting this out.... took my notebook out and put
> it in my truck, son took my truck..... or if you don't like that one....
> my dog ate my papers..... had to use the paper to write an emergency note
> for an elderly couple.....
>